THESE VENT ATMOSPHERICALLY, MEANING WATER WILL LEAK FROM THE VENT PORT!Some leak more than others. Installers must use their Fitting and Tubing of choice to run to a floor drain or drain saddle, see related items below the table. This will satisfy the bureaucrat that is stopping you from making coffee & beverage. Failure to read and follow the installation instructions, is a failure! Click here for Product Info and Installation Instructions
Certified to ANSI/NSF Standard 18, Manual Food and Beverage Dispensing Equipment
ASSE 1022 Approved Dual Check with Atmospheric Vent
316 stainless steel body for corrosion resistance
All rubber compounds comply with FDA food additive regulations
Streamlined body design minimizes pressure loss and cavitation
Endurance tested for more than 500,000 pumping cycles
Atmospheric port provides visual indication of failure of the second check
Wye-pattern strainer model for water supply installations
All materials in contact with the potable water are in compliance with the requirements of the Safe Drinking Water Act, Public Law 93-523, National Interim Primary Drinking Water Regulations.
Strainer manufactured from NSF-approved acetal plastic
Scroll down to bottom of page for more info and Installation.
Size x Size
Click here for Product Info and Installation Instructions Series SD3 is a dual check with atmospheric port designed for the protection of the water supply from carbon dioxide gas and carbonated water. These substances can flow from post-mix beverage systems and are very acidic. If the acidic water comes in contact with copper tubing or copper pipe, it will cause the leaching of copper salts into the water supply. The dissolved copper if ingested can cause nausea, abdominal pain, and in some cases vomiting.
The SD3 prevents the reverse flow of potentially contaminated water into the potable water supply. The SD3 atmospheric vent provides a visual indication of failure in the event that the downstream check fails and system back-pressure exceeds the supply pressure.
Watts SD3 is recommended for use on Post-Mix Carbonated Beverage Equipment and equipment for tea and coffee.
Installation InstructionBefore installing, flush out pipe lines to remove
scale and other foreign matter. The valve can be
installed horizontally or vertically (flow up or down).
Install the valve in the line with the arrow on the
valve body pointing in the direction of flow.
Connect a vent discharge line to the vent outlet of
the SD3 and vent to a safe place of disposal with
adequate ventilation. The valve should be installed
such that the strainer and the valve are accessible
for service and maintenance.
*Local Will Call Hours: 9:00am - 3:00pm Pacific *DUE TO INSURANCE PURPOSES, LOCAL WILL CALL ORDERS MUST BE PLACED VIA THE WEBSITE. We will pull your order and have it ready for you to pick-up within Will Call hours.
Please allow at least 1 (one) hour to process your order after it has been placed prior to will call. (Select "Local Will Call" when prompted to choose a Shipping Method; Email IPS if this option is not available)
All Will Calls/Pick Ups and Deliveries are at the "Man Door" on Side of Building @ Shipping Department.